Building Design - 2016 Code Criteria
Applicable Codes and Standards
2016 California Building Code (based on the 2015 International Building Code)
2016 California Residential Code (based on the 2015 International Residential Code)
2016 California Electrical Code (based on the 2014 National Electrical Code)
2016 California Plumbing Code (based on the 2015 Uniform Plumbing Code)
2016 California Mechanical Code (based on the 2015 Uniform Mechanical Code)
2016 California Fire Code (based on the 2015 International Fire Code)
2016 California Green Building Standards
2016 California Energy Efficiency Standards
Seismic Design Categories, SDC, are based on specific site locations. Values for spectral response accelerations, S1 and SS, and damped spectral response accelerations, SD1 and SDS, may be determined at the US Seismic Design Maps tool . These values, along with the risk category (most buildings in Santa Cruz County will be Risk Category I, II or III, with residences as Risk Category II), will determine the SDC. Most of Santa Cruz County will be SDC D or E. Use site soil Class D, unless a geotechnical report determines otherwise. For structures required to have a structural analysis (non-conventional), See ASCE Standard 7-10, Chapter 11, for complete Seismic Design Criteria.
Vult is 110 mph for Risk Category II buildings (most buildings). Exposure categories B (urban and suburban areas), C (open terrain with scattered obstructions or areas that are not Exposure B or D) or D (unobstructed areas and ocean front areas). For structures required to have a structural analysis (non-conventional), See ASCE Standard 7-10, Chapter 26, for complete Wind Design Criteria
Those areas mapped in a State Responsibility Area, SRA, shall comply with the Materials and Construction Methods for Exterior Wildfire Exposure in CBC, Chapter 7A for non-residential and CRC R337 for one and two family dwellings and townhomes. The county's GIS will determine if a project is in a State Responsibility Area, SRA. See WUI Codes for CBC 7A requirements, which generally mirror CRC R337 requirements.
For energy compliance, use Climate Zone 3. See the California Energy Commission's website.